for Anaheim, CA
Blanche - Anaheim, CA
Mark D - Anaheim, CA
blower motor not coming when thermostat calls for heat or AC. Replaced main control board, check all operation and everything is working good at this time.
Furnace was red flag by gas company
replace ac, replace furnace, rebates, financing, ac not blowing cold, condenser not coming on, compressor not working, new compressor
old AC, not blowing cold, ac making loud noise, ac not working
Installed a new Carrier 5 ton variable speed condenser 20+SEER (24VNA0), Carrier 100,000 BTU modulating variable speed furnace (59MN7), ADP high efficiency coil, all new R-8 ducts and Carrier Infinity control thermostat. Carrier rebates, SoCal Gas rebates, Anahiem rebates. City permits and HERS testing.
General Maintenance and install grill return